Drain evaporator EVAPRO
Available from 3 evaporation methods
3 different evaporation methods you can choose
Vaporization type with absorbent filter
Air inhaled by the fan is sent to the Absorbent filter to evaporate water there passing through the filter. Filter replacement time is readily visible and replacement can be done easily. Small-sized, light weight and low energy consumption. Most suitable to thermoelectric coolers/dehumidifiers.
Ultrasonic atomization type
Ultrasonic vibrator breaks up of water into droplets to discharge it into the air, where those atomized particles evaporate. Processes 650ml water per hour (at 30℃,60%RH) with only one-seventh energy consumption of heater type.
Heater type can process drain water up to 10000ml per hour (at 30℃,60%RH). Suitable for an application where large amount of water is discharged. Dual protection against over heating with thermostat and thermal fuse.
Reference chart for selection
|Processing method||Vaporization type with absorbent filter||Ultrasonic atomization type||Heater type|
|Processing power *1||20ml/h||40ml/h||320ml/h||650ml/h||1000ml/h|
|Rated voltage||24VDC±10％||Single phase, 100V-240VAC±10％||Single phase, 200VAC±10％|
|Power consumption||1.5W *2||3W *2||5W *2||5W *2||900W *3|