|Environment of use||Type of mounting||Processing method|
|EU RoHS||China RoHS||CE||UL||CSA||PSE|
|Type of mounting||Floor standing or lateral mounting|
|Processing capacity(*1)||1000ml/h (at 30℃, 60%RH)|
|Rated voltage||Single phase, 200VAC|
|Working temperature||0 to +50℃|
|Working humidity||35 to 85％RH, free from condensation|
|Error output||Overflow alarm (No voltage contact output) Contact capacity 200VAC 10A Resistance load|
|Protective function||Double safeguard against
|Thermostat (Auto-return at 45℃)|
|Thermal fuse (Fusing at 86℃)|
|Overcurrent/leakage protection by earth leakage breaker|
|Evaporation method||Direct evaporation method by heating water|
|Conformity to standards||Environment||RoHS|
- Supply voltage should be within the specified range with fluctuation not exceeding ±10%.
A complete set of supply
Washer : 4 pcs. Spring washer : 4 pcs. Hose band : 1 pc.
Instruction manual : 1 copy
|Replacement fan||Replacement filter|
・Locate EVAPRO at least 200 mm away from adjacent components or walls to keep smooth air circulation. Failure to this will lead to performance decline or adverse effect on other components.
・Do not use this product in a place where oil fumes, flammable/corrosive gasses or any matters that can destroy insulation generate or permeate.
・The site of use should be free from vibration and impact.
・Electrical works required for installation of this product should be done only by professionals or qualified personnel.
・Do not disassemble or tamper.
・Make sure that the packaging is not damaged on delivery. Any packaging damage can lead to breakdown of the product. Please contact us immediately if any damage is found.