International model Standard 220VAC Slim type
|Type of mounting||Environment||Cooling method||Functions|
|Lateral/Rececced||Duct kit (Option)||Adjustable louver (Option)||Indoor||Compressor||Energy-saving mode||Display|
|EU RoHS||China RoHS||CE||UL||CSA||PSE|
|Type of mounting||Lateral mounting|
|Cooling capacity *1||280W|
|Rated voltage（50Hz）||Single phase 220VAC|
|Current consumption *2||Rated||1.0A|
|Power consumption *2||Rated||210W|
|Comp. motor output||200W|
|Working temperature *3||＋20 to ＋50℃|
|Working humidity||Not exceeding 85％RH, free from condensation|
|Temp. setting range *3||＋30 to ＋45℃ （Initial setting +35℃）|
|Display||Innter temperature/Alarm code/Operation lamp/Alarm lamp|
|Functions||Off-temperature alarm, Detection of abnormal heat dissipation, Detection of temperature sensor disconnection, Maintenance reminder, Forced cooling operation for inspection|
|External output||Alarm output 1a 240V 1.5A×2（COMMON）|
|Vibration withstand||Vibration frequency 10 to 55Hz, Amplitude 0.15mm, Sweep cycle 10 times|
|Protection category *4||Internal circuit IP54 equivalent|
|Conformity to standards||EMC Directive||-|
*2 Nominal values at 35℃ temperature both inside and outside are indicated in “Rated” and values at 50℃ outside and 35℃ inside are indicated in “Max”.
*3 Use only within the specified temperature range.
*4 Except drain pipe
*5 By IPCC 4th Report 2007
A complete set of supply
●Nut：6 pcs ●Packing：1 roll ●Drain hose：1 pc（2m） ●Terminal board：1 pc
●Alarm explanation sheet：1 sheet ●Instruction manual：1 copy
|Replacement fan||Replacement filter|
|Internal fan model||FM-11938P-A220-00||CF-S1
|External fan model||FM-15138M-A220-00|
- Click the image to see a larger version.
- Please refer to "Model Selection for enclosure cooler" when you see the performance diagram.
・Failure to this may degrade cooling performance of the unit and cause condensation.
・Setting temperature should be basically at 35℃. Avoid setting at an unnecessarily low value.
・Electrical connection should be made via appropriate circuit breakers.
・Do not use this product in the following places.
--A place where corrosive or flammable gases exist in the air, or where the insulation destruction occurs
--A place where the product may be subject to shock or vibration.
・Make sure that electrical wiring work is done by qualified electrician.
・Check for damage on packaging when the product is delivered.
・Any packaging damage may be a cause of malfunction. Make sure that the packaging is not damaged on delivery and contact your supplier.
・Disposal of refrigerant and oil sealed in the cooling circuit should be dealt with only by professional services.